Последний раз этот стандарт был пересмотрен в 2020. Поэтому данная версия остается актуальной
ISO 17918:2015 specifies procedures of on-site detection and evaluation in order to determine the effects of material deterioration such as material loss from the components and structures that are sensitive to selective corrosion in industrial facilities, including nuclear power plants.
The methodology involves visual inspection and hardness measurements in situ complemented by sample removal. These procedures include (a) representative sampling of components sensitive to selective corrosion, (b) the visual inspection, and (c) the hardness test, respectively. For an exact analysis, additional laboratory testing is recommended.
The methodology is most applicable to grey cast iron and copper alloy with more than 15 % zinc. Extension to other alloys requires supportive evidence of validation.
Assessment criteria orientated to the nuclear power plant application during the past five years before the end of extended operation define the necessity for further engineering evaluation and action like, for example, further sampling, higher frequency of inspection, and component repair or exchange.
This specification is not applicable for components used where the representative sampling of surfaces in contact to the fluid is not detectable optically or detected with the portable hardness tester. Also, in case of non-representative component selection like in HVAC or building service application, this specification is not applicable. For components not used in nuclear power plant, the assessment criteria have to be agreed by the parties. Assessment criteria of hardness test alone is not applicable to the evaluation of structural integrity of Al-bronze, NAB, and Cu-Ni.
Текущий статус : PublishedДата публикации : 2015-07
Версия : 1
Технический комитет:Corrosion of metals and alloys
Приобрести данный стандарт