This standard was last reviewed* in 2014.
ISO 14694:2003 gives specifications for vibration and balance limits of fans for all applications except those designed solely for air circulation, for example, ceiling fans and table fans. However, it is limited to fans of all types installed with a power of less than 300 kW or to commercially available standard electric motor with a maximum power of 355 kW (following an R20 series). For fans of greater power than this, the applicable limits are those given in ISO 10816 - 3. Where the fans in an installation have varying powers both above and below 300 kW, and have been the subject of a single contract, then the manufacturer and purchaser shall agree on the appropriate standard to be used. This should normally be based on the majority of units.
Fan-equipment foundations and installation practices are beyond the scope of ISO 14694:2003. Foundation design and fan installation are not normally the responsibilities of the fan manufacturer. It is fully expected that the foundations upon which the fan is mounted will provide the support and stability necessary to meet the vibration criteria of the fan as it is delivered from the factory.
ISO 14694:2003 is intended to cover only the balance or vibration of the fan and does not take into account the effect of fan vibration on personnel, equipment or processes.
Document published on: 2003-03-15 Edition: 1 (Monolingual) ICS: 23.120; 21.120.40 Status: Published Stage: 90.93 (2014-04-25) TC/SC: ISO/TC 117 Number of Pages: 39
No revision information available